Notifier SCS-8 (NEW)
The SCS-8 Smoke Control Station and optional SCE-8 Smoke Control Expander, SCS-8L Smoke Control Lamp Driver, and SCE-8L Smoke Control Lamp Driver Expander are used with the Notifier AM2020/AFP1010, NFS-640, NFS-3030, NFS2-3030 Fire Alarm Control Panels (FACPs), NCA or NCA-2 Network Control Annunciator displays, or the INA, to provide the capability to control and display the status of AHU fans or dampers. Each SCS can control and monitor eight AHU fans or dampers. The SCS-8L and SCE-8L must be installed in a UL-Listed Graphic Annunciator backbox. The SCE is used with the SCS, expanding the capability to control and monitor a total of 16 AHU fans or dampers. Only one SCE can be used for each SCS and a maximum of 32 pairs can be used with each Notifier control panel. With the maximum configuration of 32 pairs, the system has the capability to control and monitor 512 separate AHU fans or dampers. The SCS can be used with the Intelligent Network Annunciator (INA) Release 2.8 (or higher) and with the NFS-640 (without NCA display option) in HVAC mode only.
The SCS/SCE, when used with the AM2020/AFP1010, NFS(2)-3030, or NCA(-2) display with ONYX® Series FACPs, complies with UL smoke control requirements (Category UUKL) for dedicated and non-dedicated systems as well as NFPA 90A, 92A, and 92B standards for smoke control. The SCS/SCE also complies with UL 916 Energy Management category PAZX.